Provide for pressure balancing between bedrooms and the rest of the house.
- Install ducted returns or a combination of ducted returns, transfer grilles, jump ducts, and/or door undercuts in bedrooms to allow pressure balancing between bedrooms and the rest of the house in homes with ducted heating and cooling systems by providing a path for stale air to return to the return side of a central air handler.
- ENERGY STAR Certified Homes requires that the dedicated return ducts, transfer grilles, jump ducts, and/or door undercuts provide 1 square inch of free area opening per 1 CFM of supply air, as reported on the contractor-provided balancing report. Or, that the dedicated return ducts, transfer grilles, jump ducts, and/or door undercuts together achieve a Rater-measured pressure differential of ≤3 Pascals (0.012 inch water column) with respect to the main body of the house when bedroom doors are closed and the air handler is operating.
- If dedicated return ducts are installed in each bedroom, contractors must seal all seams, gaps, and holes of the return duct system with mastic and seal the return box to the floor, wall, or ceiling with mastic, caulk, and/or foam.
- If transfer grilles or jump ducts are used, refer to the balancing report provided by the HVAC contractor for the bedroom air flows to size the grilles or ducts. Ensure that both openings have the required free area. Seal all seams, gaps, and holes in the ducts and connections.
- If door undercuts are used, framers should cut the bottom of the doors to approximately ¾ inch above the finished floor.
- Test the pressure differential with the bedroom doors closed.
See the Compliance Tab for related codes and standards, and criteria to meet national programs such as ENERGY STAR Certified Homes, DOE’s Zero Energy Ready Home program, and EPA’s Indoor airPLUS.
No climate specific information applies.
ENERGY STAR Certified Homes (Version 3/3.1, Revision 08), Rater Field Checklist:
6. Duct Quality Installation
6.2 Bedrooms pressure-balanced using any combination of transfer grills, jump ducts, dedicated return ducts, and / or undercut doors to achieve a Rater-measured pressure differential ≤ 3 Pa with respect to the main body of the house when all bedroom doors are closed and all air handlers are operating. See Footnote 34 for alternative.34
34. Item 6.2 does not apply to ventilation or exhaust ducts. For an HVAC system with a multi-speed fan, the highest design fan speed shall be used when verifying this requirement. As an alternative to the 3 Pa limit, a Rater-measured pressure differential ≤ 5 Pa is permitted to be used for bedrooms with a design airflow ≥ 150 CFM. The Rater-measured pressure shall be rounded to the nearest whole number to assess compliance.
Builders Responsibilities: It is the exclusive responsibility of builders to ensure that each certified home is constructed to meet these requirements. While builders are not required to maintain documentation demonstrating compliance for each individual certified home, builders are required to develop a process to ensure compliance for each certified home (e.g., incorporate these requirements into the Scope of Work for relevant sub-contractors, require the site supervisor to inspect each home for these requirements, and / or sub-contract the verification of these requirements to a Rater). In the event that the EPA determines that a certified home was constructed without meeting these requirements, the home may be decertified.
ENERGY STAR Revision 08 requirements are required for homes permitted starting 07/01/2016.
Associated Air Barrier Council 2002. AABC National Standards for Total System Balance 2002. The manual details the minimum standards for total system balance.
National Environmental Balancing Bureau (NEBB) Section 15990 – Testing, Adjusting, and Balancing. NEBB is a certification association whose members perform testing, adjusting and balancing (TAB) of heating, ventilating, and air-conditioning systems and commission and retro-commission building systems. This document is the TAB procedural standards.