Provide an architectural drawing and riser diagram for the homeowner showing the planned location for future photovoltaic and solar hot water system components. Space requirements and layout for photovoltaic and solar water heating system components should be taken into account early in the design process.
See the Compliance Tab for related codes and standards requirements, and criteria to meet national programs such as DOE’s Zero Energy Ready Home program, ENERGY STAR Single-Family New Homes, and Indoor airPLUS.
A renewable energy-ready home (RERH) is one that is built with the wiring and plumbing conduit and other components in place to facilitate the future installation of solar photovoltaic (PV) panels and/or solar water heating panels. Some energy-efficiency programs, like the U.S. Department of Energy’s DOE Zero Energy Ready Home Program, require homes to be renewable-energy ready.
To meet the requirements of the DOE Zero Energy Ready Home program, provide an architectural drawing and riser diagram of RERH solar PV system components and solar hot water.
Develop architectural drawings and diagrams that summarize the installed system equipment (conduit, etc.) as detailed below (see Figure 1). These drawings should accurately represent the installed elements of the system and should be provided to the homeowner (likely to be used by future solar installer for obtaining a building permit). In addition, the homeowner should be provided with a one-line electrical riser diagram of the PV system components. The diagram should have sufficient detail to clearly identify:
- Configuration of the PV array
- Conduit size and type
- Electrical service panel location and dedicated circuit breaker slots
- Length of conduit from the designated array location to the designated inverter location
- Location and number of necessary pull boxes in line with each conduit run
- Length of conduit from the designated inverter location to the electrical service panel
- Location of the Balance-of-System (BOS) components
The drawings should also contain information about the PV array mounting system and identify the specifications for the major equipment including manufacturer, model and installation details.
When designing the system, always follow the recommendations of all local and national codes as well as manufacturer’s recommendations.
Ensure adequate utility room early in the house design process to allow for ample space for solar photovoltaic (PV) and water heating system components. Confirm with local code officials early in the design process what steps are needed to guarantee that installation of PV panels will meet with local codes, homeowner's association covenants, and historic district regulations.
Protect the electrical and mechanical components of the PV system from bulk moisture, high temperatures, and direct sunlight. The utility room should be properly ventilated and maintain average indoor temperatures. Proper clearances and working spaces should also be maintained.
The DOE Zero Energy Ready Home PV-Ready Checklist (Revision 07) is required only under the following condition related to climate (See the Compliance Tab for other exceptions):
- Location, based on zip code, has at least 5 kWh/m2/day average daily solar radiation based on annual solar insolation using the PVWatts online tool. See map below.
The Compliance tab contains both program and code information. Code language is excerpted and summarized below. For exact code language, refer to the applicable code, which may require purchase from the publisher. While we continually update our database, links may have changed since posting. Please contact our webmaster if you find broken links.
Exhibit 1 Mandatory Requirements.
Exhibit 1, Item 1) Certified under the ENERGY STAR Qualified Homes Program or the ENERGY STAR Multifamily New Construction Program.
Exhibit 1, Item 7) Provisions of the DOE Zero Energy Ready Home PV-Ready Checklist are Completed.
Provide architectural drawing of solar PV system components. (RERHPV Guide 3.5)
Alternative: Provide home buyer with the following information:
- List of renewable-ready features
- Available free roof area within +/- 45° of true south
- Location of panel or blocking for future mounting of PV system components
- Location of Breaker or slot for future breaker in electrical service panel
- Copy of the PV-Ready Checklist
- A copy of the RERH Solar PV Specification Guide
Footnote 18) DOE Zero Energy Ready Home requires that the provisions of the PV-Ready Checklist are completed based on the requirements and allowances in this end note. For multifamily buildings, the PV-Ready provisions may be applied to the electric service for the building’s common space instead of being applied to each dwelling unit. DOE encourages, but does not require, the use of the Solar Water Heating-Ready provisions.
The PV-Ready Checklist only applies when all of the following conditions 1 through 4 below are satisfied. Homes for which the PV-Ready Checklist does not apply based on these criteria may still qualify for DOE Zero Energy Ready Home if all other program requirements are satisfied. Homes that utilize renewable energy from utilities or third parties on a contractual basis may also be exempt from the PV-Ready Checklist – contact DOE for further guidance.
- The home does not already include a PV system. This includes installed community solar systems which contribute some amount of offset to the home’s electrical usage.
- Location, based on zip code, has at least 5 kWh/m2 /day average daily solar radiation based on annual solar insolation using this online tool: PVWatts Calculator. Users should enter the project location zip code, use the System Info default settings, and then proceed to the “Results” tab on the tool to see the Average Annual Solar Radiation value in kWh/m2 /day.
- Location does not have significant natural shading (eas designed has the minimum free roof area within +/- 45◦ of true south as noted in the table below. Note that in some cases a house may have insufficient roof area for the Solar Electric RERH checklist, but it may still have the minimum roof area for the solar thermal RERH Checklist and would therefore have to comply with the Solar Thermal RERH checklist. In other cases, the home may only have adequate south facing roof for the Solar Electric or Solar Thermal RERH Checklist, but not both. In that case the builder can decide which one of those two checklists to apply (e.g., trees, tall buildings on the south-facing roof).
- Home as designed has the minimum free roof area within +/- 45◦ of true south as noted in the table below.
Community Solar - If a home is served by a community solar system, it does not have to meet the PV-Ready Checklist provisions.
Multifamily - For multifamily buildings, the PV-Ready provisions may be applied to the electric service for the building’s common space instead of being applied to each dwelling unit.
Section R401.3 A permanent certificate shall be posted on or near the electrical distribution panel that lists types and efficiencies of water heating, heating, and cooling equipment, as well as insulation R values, and window U and SHGC factors.
Section R101.4.3 (in 2009 and 2012). Additions, alterations, renovations, or repairs shall conform to the provisions of this code, without requiring the unaltered portions of the existing building to comply with this code. (See code for additional requirements and exceptions.)
Chapter 5 (in 2015, 2018, 2021). The provisions of this chapter shall control the alteration, repair, addition, and change of occupancy of existing buildings and structures.
M2301 Solar Energy Systems (Solar Thermal Energy Systems in 2015, 2018, and 2021 IRC) - See requirements for solar water heating systems.
Section R102.7.1 Additions, alterations, or repairs. Additions, alterations, renovations, or repairs shall conform to the provisions of this code, without requiring the unaltered portions of the existing building to comply with the requirements of this code, unless otherwise stated. (See code for additional requirements and exceptions.)
Appendix J regulates the repair, renovation, alteration, and reconstruction of existing buildings and is intended to encourage their continued safe use.
Follow the requirements for solar photovoltaic (PV) systems found in the 2014 National Electric Code (NEC), Article 690, PV Power Systems, and Article 110, Requirements for Electrical Installations.
Access to some references may require purchase from the publisher. While we continually update our database, links may have changed since posting. Please contact our webmaster if you find broken links.
As solar photovoltaic (PV) panels have significantly come down in price, many homeowners are installing them to produce clean power and reduce their electric bills. Many more homeowners are likely to want this option for the future. Solar electric-ready homes make this possible with minimal to no disruption or cost penalty using simple no-cost/low-cost details and best practices integrated during construction. This includes ensuring adequate unshaded roof space for the PV panels, installing conduit from the attic to the electric service panel, securing documentation that the roof is designed to support the extra weight of the PV array, and providing adequate space near the electrical panel for balance of system components.