To construct a home that is prepared for the installation of a future solar photovoltaic (PV) system:
- Include a dedicated 70-amp dual-pole circuit breaker.
- Place the circuit breaker panel box near the future balance of system components for the PV.
- Consider space requirements and layout within the home and on the roof for solar photovoltaic system components early in the design process.
See the Compliance Tab for related codes and standards requirements, and criteria to meet national programs such as DOE’s Zero Energy Ready Home program, ENERGY STAR Single-Family New Homes, and Indoor airPLUS.
A renewable energy-ready home (RERH) is one that is built with the wiring and plumbing conduit and other components in place to facilitate the future installation of solar photovoltaic (PV) panels and/or solar water heating panels. Some energy-efficiency programs, like the U.S. Department of Energy’s DOE Zero Energy Ready Home Program, require homes to be renewable-energy ready.
To prepare for a future PV system to be connected in a home, install a dedicated double-pole circuit breaker in the electrical service panel or in a separate subpanel. The breaker is intended for protection of the PV modules and wiring from reverse current flow. The breaker should be appropriately sized for the PV array that is being installed.
How to Install a 70-Amp Dual-Pole Circuit Breaker
- To meet the requirements of the DOE Zero Energy Ready Home program, designate a dedicated space in the electrical service panel for a dual-pole circuit breaker.
- Hire a licensed electrician certified by the local jurisdiction to install the electrical equipment associated with the electrical service panel.
- Label each breaker in the service panel with water-resistant labels. The breakers dedicated for the future PV system should read, “Renewable Energy Ready Home – Solar PV Dedicated Breaker.” See Figure 1.
- Record the location of the future PV system and all of its components on relevant architectural diagrams to be provided to the homeowner.
Ensure adequate space in the electrical service panel for a dedicated dual-pole breaker, early in the design process. If possible, place the circuit breaker panel box near the future balance of system components for the PV. Confirm with local code officials early in the design process what steps are needed to guarantee that installation of PV panels will meet with local codes, homeowner's association covenants, and historic district regulations.
Protect the electrical and mechanical components of the PV system from bulk moisture, high temperatures, and direct sunlight. The utility room should be properly ventilated and maintain average indoor temperatures. Proper clearances and working spaces should also be maintained.
The DOE Zero Energy Ready Home PV-Ready Checklist (Revision 07) is required only under the following condition related to climate (See the Compliance Tab for other exceptions):
- Location, based on zip code, has at least 5 kWh/m2/day average daily solar radiation based on annual solar insolation using the PVWatts online tool. See map below.
The Compliance tab contains both program and code information. Code language is excerpted and summarized below. For exact code language, refer to the applicable code, which may require purchase from the publisher. While we continually update our database, links may have changed since posting. Please contact our webmaster if you find broken links.
Exhibit 1 Mandatory Requirements.
Exhibit 1, Item 1) Certified under the ENERGY STAR Qualified Homes Program or the ENERGY STAR Multifamily New Construction Program.
Exhibit 1, Item 7) Provisions of the DOE Zero Energy Ready Home PV-Ready Checklist are Completed.
- Install a 1” metal conduit for the DC wire run from the designated array location to the designated inverter location (cap and label both ends). (RERHPV Guide 3.2)
- Install a 1” metal conduit from designated inverter location to electrical service panel (cap and label both ends). (RERHPV Guide 3.3)
- Install and label a 4’ x 4’ plywood panel area for mounting an inverter and balance of system components. (RERHPV Guide 3.1)
Alternative: Blocking is permitted to be used as an alternative to the 4’ x 4’ panel. The area designated for the future panel to mount PV components shall be clearly noted in the system documentation.
- Install a 70-amp dual pole circuit breaker in the electrical service panel for use by the PV system (label the service panel) (RERHPV Guide 3.4)
Alternative: Provide a labeled slot for a double-pole breaker in the electrical service.
DOE Zero Energy Ready Home National Program Requirements Mandatory Requirement 7 (Renewable Ready) shall be met by any home certified under the DOE Zero Energy Ready Home program, only where all of the following conditions are met:
- Location, based on zip code has at least 5 kWh/m2/day average daily solar radiation based on annual solar insolation using PVWatts online tool, AND;
- Location does not have significant natural shading (e.g., trees, tall buildings on the south-facing roof, AND;
- Home as designed has adequate free roof area within +/-45° of true south as noted in the table below.
Community Solar - If a home is served by a community solar system, it does not have to meet the PV-Ready Checklist provisions.
Multifamily - For multifamily buildings, the PV-Ready provisions may be applied to the electric service for the building’s common space instead of being applied to each dwelling unit.
Follow the requirements for solar water heating systems found in the IMC, Chapter 14, Solar Thermal Systems ("Solar Systems" in 2009, 2012, and 2015 IMC).
Follow the requirements for solar photovoltaic (PV) systems found in the 2014 National Electric Code (NEC), Article 690, PV Power Systems, and Article 110, Requirements for Electrical Installations.
For a gut rehab where the objective is to renovate the home to meet the criteria of the DOE Zero Energy Ready Home program or a similar program that requires the home to be ready for the installation of solar panels, follow the new home guidance provided in the Description tab.
For a renovation that includes installation of photovoltaic solar panels on an existing home, verify with the panel installer that the electrical panel has sufficient space and backfeed protection for the photovoltaic system desired.
Access to some references may require purchase from the publisher. While we continually update our database, links may have changed since posting. Please contact our webmaster if you find broken links.
As solar photovoltaic (PV) panels have significantly come down in price, many homeowners are installing them to produce clean power and reduce their electric bills. Many more homeowners are likely to want this option for the future. Solar electric-ready homes make this possible with minimal to no disruption or cost penalty using simple no-cost/low-cost details and best practices integrated during construction. This includes ensuring adequate unshaded roof space for the PV panels, installing conduit from the attic to the electric service panel, securing documentation that the roof is designed to support the extra weight of the PV array, and providing adequate space near the electrical panel for balance of system components.