Proper Installation of Filter
No climate specific information applies.
Air filters are an important component of forced air HVAC systems. Filters are installed on the return side of the HVAC air handler to clean the air to protect the HVAC motor and to improve indoor air quality. Filters should also be installed in fresh air intakes to clean outside air that is brought into the home. Filters with higher MERV (Minimum Efficiency Reporting Value) ratings of MERV 6 or above can trap pollutants like pollen, dust mites, and mold spores. However, a dirty, clogged filter can dramatically reduce air flow, increasing furnace run time and increasing both wear on the motor and energy consumption. For optimum operation of both the filter and the HVAC equipment, the filters should be replaced or cleaned frequently. Therefore, the filters should be located in a place that is easily accessible for the home owner.
If the furnace air handler is in an accessible location (such as a utility room, a basement, or an attic with a pull-down staircase), the filter can be installed in the air handler at the return plenum. The air handler box should be equipped with a filter media box that has a removable access panel cover that has a gasket for an air-tight seal when closed. The filter box might be prefabricated by the manufacturer or could be fabricated on site. The filter media frame should be appropriate for the size and type of filter desired. The filter dimensions and filter depth both influence filter capacity and air flow velocity. Filter sizing must be taken into account when designing the HVAC system to ensure that the HVAC system can handle the associated pressure drop, especially with high MERV filters. Increasing the filter surface area will decrease pressure drop; options for increasing surface area could include using more deeply pleated filters or larger dimensioned filters. Filters must be sized using the Air Conditioning Contractors of America (ACCA) Manual D (ANSI/ACCA 2009). For more on furnace filter MERV ratings and sizing, see High MERV Filter.
If the furnace is in the attic, in addition to a staircase or pull-down stairs, there should be a permanently installed walkway for the homeowner or service technician to use to get to the furnace.
If the furnace air handler is located in an inaccessible location such as a crawlspace or attic without a staircase, then the furnace filters should be located in the return grilles, with a filter located in each return grille.
If the home is equipped with a fresh air intake that is ducted to the air handler, a filter should be installed at the fresh air intake and the fresh air intake should be located where it is accessible so the filter can be replaced or cleaned as needed.
One Option for Increasing Filter Surface Area
If the furnace is in a location where it can be accessed by the homeowner for filter replacement and where the furnace location permits an increase in the width of the return duct, the following option may enable the installation of higher MERV filters.
- Calculate pressure drop and airflow requirements for the desired filter MERV and dimensions in accord with Manual D (ANSI/ACCA 2009). Construct a box to hold two filters side-by-side in the return duct above the 90 degree turn into the return air plenum. Increase the duct width to accommodate the filter dimensions above and below this filter box. If possible, install the filter box at shoulder height for easier servicing. See the figure below.
Figure 3 - To increase surface area and reduce pressure drop for high MERV filters, the return duct can be constructed to permit the installation of two furnace filters side by side, if space at the HVAC installation permits and if the HVAC location makes filter replacement practical.
How to Install a Filter in a Furnace Air Handler
1. Fabricate and install a filter media box on site. Install the filter media box between the return air plenum and the air handler box. Or, purchase an air handler that includes a pre-fabricated filter box. Ensure that the box is the right size for the filter to be installed. Filters must be sized using ACCA Manual D (ANSI/ACCA 2009). Improperly sized filters can cause mechanical failure.
2. Slide the filter into place and place the filter access panel cover over the opening. The panel cover should have a gasket to ensure an air-tight seal. The cover can be duct taped at the edges, which provides additional air sealing and can be easily removed when the filter is checked for cleaning or replacement. If the filter cover is left off or unsealed, the air handler can pull unconditioned and/or unwanted air into the home. Leakage at the filter cover can be an indoor air quality problem if the air handler is located in a garage or other areas where the air quality is not desirable.
3. Complete air handler installation by installing wiring and condensate piping. Ensure that piping and wiring do not block access to the filter.
How to Install a Filter at the Return Grille
1. If the furnace is in a location that is difficult for the homeowner to access (for example, a crawlspace or an attic that does not have stairway or drop-down stairway access), then install filters inside the return grilles in the home.
2. Ensure that grilles can be opened from within the home. Install grilles that can be removed safely, for example, grilles that are attached by a hinge along one side to minimize the risk that they will accidentally fall down while being opened.
3. Install MERV 6 or higher filters that match the sizing designation specified by the HVAC designer in accord with Manual D (ANSI/ACCA 2009). Do not install filters with MERV ratings higher than that for which the HVAC system was designed. Higher-than-specified MERV filters will increase air resistance, increasing energy usage and possibly contributing to equipment failure. For more about filter sizing, see High MERV Filter.
How to Install a Filter at the Fresh Air Intake
Choose a location to install the outside air intake, such as a porch ceiling or eave, that is away from polluting sources and easily accessible to the home owner to facilitate filter replacement (see Figures 2 and 9). For more on outside air intake locations, see Ventilation Air Inlet Locations.
Cut a hole for the air intake with dimensions similar to the grille and the filter to be installed. When selecting a filter size and MERV rating, consider air flow resistance because the pressure drop of this outdoor air intake duct and filter must be included in the Manual D calculations when designing the entire HVAC duct system. A MERV 6 filter should be adequate.
Install a register box (boot) to which the duct will be attached. Most register boxes are at least 4 inches deep. This space will keep the duct terminus from touching the filter. Allowing several inches of distance between the filter and the duct terminus helps to decrease the velocity of the air flow through the filter and also ensures that the full surface area of the filter is used, which will improve filter performance and increase filter life.
Install a hinged grille at the exterior of the fresh air intake opening (see Figure 8).
Cover the grill with wire mesh insect and bird screen.
Place the filter on the interior side of the grille and close the grille.
Include instructions informing the homeowner to check this filter periodically for replacement with a similar MERV-rated filter.
If the outside air intake must be located in an inaccessible location, construct and install a filter media frame in a filter box that is positioned in an accessible place at the duct connection to the air handler return air plenum or somewhere along the fresh air intake duct that is accessible to the home owner.
In homes with ducted HVAC equipment, the designer/ HVAC contractor should specify and install furnace filters at the return plenum of the air handler or at all return grilles and on any outdoor air intakes. The HERS rater should inspect to make sure that the filters are installed correctly; if the filter is installed at the furnace, inspect that a filter media box has been installed to house the filter and that this box has an access panel with a gasket to prevent air leakage.
All return air and mechanically supplied outdoor air pass through filter prior to conditioning.
- Install filters in the proper locations of the HVAC system.
- Install filters at all outdoor air intakes.
Filter located and installed so as to facilitate access and regular service by the owner.
- If the HVAC equipment is placed in an accessible location, such as a basement, filters should be installed adjacent to the equipment.
- If the HVAC equipment is placed in an inaccessible location, such as a crawlspace, install filters in an accessible location, such as a return box.
Filter access panel includes gasket or comparable sealing mechanism and fits snugly against the exposed edge of filter when closed to prevent bypass.
- Install gaskets or frame to prevent air bypass.
ENERGY STAR Notes:
HVAC filters located in the attic shall be considered accessible to the owner if drop-down stairs provide access to attic and a permanently installed walkway has been provided between the attic access location and the filter.
The filter media box (i.e., the component in the HVAC system that houses the filter) may be either site-fabricated by the installer or pre-fabricated by the manufacturer to meet this requirement. These requirements only apply when the filter is installed in a filter media box located in the HVAC system, not when the filter is installed flush with the return grille.
HVAC System Quality Checklist, Filtration. All return air and mechanically supplied outdoor air pass through filter prior to conditioning. Filter located and installed so as to facilitate access and regular service by the owner. HVAC filters located in the attic shall be considered accessible to the owner if drop-down stairs provide access to attic and a permanently installed walkway has been provided between the attic access location and the filter. Filter access panel includes gasket or comparable sealing mechanism and fits snugly against the exposed edge of filter when closed to prevent bypass. The filter media box (i.e., the component in the HVAC system that houses the filter) may be either site-fabricated by the installer or pre-fabricated by the manufacturer to meet this requirement. These requirements only apply when the filter is installed in a filter media box located in the HVAC system, not when the filter is installed flush with the return grille.
Exhibit 1: Mandatory Requirements. Certified under ENERGY STAR Qualified Homes Version 3.
Filter installation is not specifically addressed in the 2009 IECC.
Filter installation is not specifically addressed in the 2009 IRC.
Filter installation is not specifically addressed in the 2012 IECC.
Filter installation is not specifically addressed in the 2012 IRC.